Custom pressurisation and Gas Phase filtration for Petrochemical substation.
Durbam Harbour petrochemical substation had issues with dust ingress, and corrosion damage to electrical equipment.
|Customers Problem||Petrochemical substation had issues with dust ingress, and corrosion damage|
|Plant supply Volume|| |
1.72m3/sec per fan - 5.5 kW with 1 standby Fan
|Material of Construction||304 Stainless Steel|
|Filters Installed|| |
Primary: Vilidon G35 Pocket Filters
Secondary: MVP 85 Cassette Filters
2 X 18.5 kW fans - one on standby
|Cleaning System|| |
|Primary Stage:||Viledon Chemcontrol CCP108 - 1000kg|
|Secondary Stage||Viledon Chemcontrol CCP310 - 1000kg|
|Stable Pressure Loss:||1,500Pa|
|Value to Customer|| |
Positively pressurising and Gas Phase Filtration in the one unit has resulted in no dust ingress and reduced corrosion if the electrical equipment thus extending the lifespan and lowering maintenance costs